Foul drainage assessment
Used to ensure a satisfactory standard of foul drainage.
Mains foul drainage assessment
For Major Developments incorporating foul drainage into the public sewer, we advise early discussions with United Utilities to determine whether or not a load or flow assessment should be submitted with the planning application, in order to demonstrate the impact of the development on the public sewer infrastructure.
Non-mains foul drainage assessment
Development involving either the installation of new non-mains drainage or the use of existing non-mains drainage (package treatment plants, septic tanks, cesspools). This includes domestic extensions if the foul sewage will be treated by existing or proposed non-mains system.
In order to demonstrate that the development can be effectively served by a non-mains foul drainage system without inadvertently affecting the environment, amenity or public health, a foul drainage assessment form should be submitted.
If a new non-mains foul drainage system is proposed, its position together with any associated soakaways and pipework must be shown within the application site (the red line) on the site location plan.
Percolation test results will be required where a new non-mains drainage system is proposed.
Percolation test method to calculate area of drainage field for Septic tanks or sewage treatment systems:
- Excavate a test hole 300mm square x 300mm deep below proposed invert level of the drainage field trench bottom.
- Fill the test hole with water and allow drain away over night.
- Refill to a depth of 300mm and note time taken in seconds to drain away from 75% full to 25% full (that is 150mm drop in level from 225mm to 75mm).
- Repeat the procedure in two more test holes and calculate the average of the three results as follows. Test one + test two + test three = average three time taken.
- Calculate the Vp (average time in seconds for the water to drop 1mm) as follows:
For example: If average time above took 2,700 seconds
(i) Divide 2,700 seconds by 150mm depth of water
(ii) 2,700 = 18 Vp* (see note below*)
(iii) Area of trench = number of persons to use property x Vp x 0.25.Therefore: 5 persons X 18 X 0.25 = 13.5m2 of effluent drain required.
(iv) To calculate actual length of trench divide 13.5 by width of the trench required therefore 13.5m2 = 22m (minimum permitted area is 30m 0.6m wide long x 0.6m wide).
* Vp should range between 12 and 100 to be successful; otherwise the system should be designed by a drainage specialist.
If connection to non-mains drainage requires pipework to cross land outside the applicant’s ownership, other than the public highway, the correct ownership certificate B, C or D should be completed and a notice served on the owner(s) of that land.